Type of the Pdu.
PduModular (0) Modulaire OEC2 PDU communication through SNMPV3, MOD-BUS or AP-BUS in emulation mode.
PduGateway1 (1) Gateway to connect OEC1 products with external AP-BUS protocol to OEC2 Manager (SNMPV3).
PduGateway2 (2) Gateway to connect OEC2 products with external MOD-BUS to OEC Manager (SNMPV3).
Status of the Pdu.
pduBusy (0) Indicates that an admin command is in progress.
pduReady (1) The execution of an admin command was successfull.
pduAlarm (2) This state is not in use.
pduError (3) The execution of an admin command failed.
PDU admin management Commands:
noOp (0) No operation.
rebootPdu (1) Reboot the PDU (to execute new settings).
rediscover (2) Not supported.
updateSofware (3) Not supported.
resetConfig (4) Node and group tables will be cleared .
resetSNMPv3Config (5) Not supported.
resetNetworkSetting (6) Reset network params: ip address, defualt gatewy, subnet mask.
readDataFromBusPdu (7) Read data from a PDU connected to the external bus (address is set in pduBusAddress).
writeDataToBusPdu (8) With this command modified data is writen back to the bus PDU (address is set in pduBusAddress).
Array of bits each one an specific feature within the pdu:
globalWebEnabled (0) This bit enables the PDU webpages.
globalUsbEnabled (1) This bit enables the USB menu.
globalSwitchEnabled (2) This bit enables switching in general.
displaySwitchEnabled (3) This bit enables switching through the presentation module.
webSwitchEnabled (4) This bit enables switching throuhg the web inteface.
Array of bits each one indicates an alarm activated in the alarm selector value.
TrapCurrHi (0) The current is to high against the high current threshold.
TrapCurrLo (1) The current is to low against the low current threshold.
TrapVoltHi (2) The voltage is to high against the high voltage threshold.
TrapVoltLo (3) The volage is to low against the low voltage threshold.
SwitchOn (4) The switch is on against the switch on bitfield.
SwitchOff (5) The switch is off against the switch off bitfield.
Array of bits each one controls one alarm.
TrapCurrHi (0) Enable/disable the high current alarm.
TrapCurrLo (1) Enable/disable the low current alarm.
TrapVoltHi (2) Enable/disable the high voltage alarm.
TrapVoltLo (3) Enable/disable the low voltage alarm.
SwitchOn (4) Enable/disable the specific switch on alarm.
SwitchOff (5) Enable/disable the specific switch off alarm.